Loop Design and Wiring
The fire alarm control panel Zone wire can be connected
to terminal 2(+),4(-).
And there is a 5.1V Zener diode should be connected to
terminal 1A and 4A.(included by default).
If the manual call point is in the end of the zone wire, a
5.6K resistance should be connected to terminal 2, 4.
NOTE: All wiring must conform to applicable local
codes, ordinances, and regulations.
Mounting Indoor Wall
1. Attach mounting base to wall at 1.5 meter’s high.
2. Connect field wiring to terminals
3. To attach product to mounting base.
4. Secure product by tightening the one mounting screws
in the front of the product housing.
Figure 1. Install and Wiring diagram: